http://chineseinput.net/에서 pinyin(병음)방식으로 중국어를 변환할 수 있습니다.
변환된 중국어를 복사하여 사용하시면 됩니다.
개별검색 DB통합검색이 안되는 DB는 DB아이콘을 클릭하여 이용하실 수 있습니다.
통계정보 및 조사
예술 / 패션
<해외전자자료 이용권한 안내>
- 이용 대상 : RISS의 모든 해외전자자료는 교수, 강사, 대학(원)생, 연구원, 대학직원에 한하여(로그인 필수) 이용 가능
- 구독대학 소속 이용자: RISS 해외전자자료 통합검색 및 등록된 대학IP 대역 내에서 24시간 무료 이용
- 미구독대학 소속 이용자: RISS 해외전자자료 통합검색을 통한 오후 4시~익일 오전 9시 무료 이용
※ 단, EBSCO ASC/BSC(오후 5시~익일 오전 9시 무료 이용)
김광현(Kwnag-Hyun Kim), 박지경(Ji-Kyung Park), 김준혁(Jun-Hyeok Kim), 김두웅(Doo-Ung Kim), 강성범(Sung-Bum Kang), 김철환(Chul-Hwan Kim), 유영식(Young-Sik Lyu), 양정재(Jeong-Jae Yang), 고윤태(Yun-Tae Ko) 대한전기학회 2016 전기학회논문지 Vol.65 No.8
It is important to clear the fault and prevent resulting in damage to power system. Although the frequency of generator internal fault is relatively low, it can lead to incalculable damage to power system as well as generator. Especially, loss of field on generator can cause the generator to lose synchronism for a short time if it is not removed promptly. Therefore, it is needed to conduct research on loss of field relay for detecting or clearing the loss of field. However, the setting of the relay may vary in generator operator or engineer, and the relay is not coordinated well with other elements associated with loss of field. In this paper, we address specifically the coordination of positive offset mho loss of field relay which is one of the protection schemes for loss of field. Computer simulations are performed by using ElectroMagnetic Transients Program-Restructured Version (EMTP-RV) based on actual data.
Recently, DC-based power system is being paid attention as the solution for energy efficiency. As the example, HVDC (High Voltage DC) transmission system is utilized in the real power system. On the other hand, researches on LVDC (Low Voltage DC) distribution system, which are including digital loads, are not enough. In this paper, reliability in LVDC distribution system is analyzed according to the specific characteristics such as the arrangement of DC/DC converters and the number of poles. Furthermore, power quality is also taken account of since LVDC distribution system includes multiple sensitive loads and electric power converters. In order to achieve this, LVDC distribution systems are modeled using ElectroMagnetic Transient Program (EMTP) and both the minimal cut-set method and Customer Interruption Cost (CIC) are used in the reliability analysis.